K-1 2E, K-2 2E, K-3 2E
The magnetic contacts consist of two elements: magnetic sensor (reed switch) and
magnet. The reed switch, which is situated near the magnet, makes the electric circuit.
Each of the magnetic contact elements is
placed in an identical watertight housing, the
part with reed switch having electric lead-
outs (Fig. 1,2,3). Inside the housing together with the reed switch are installed two 1.1kΩ
Fig. 1 K-1 2E reed switch in plastic housing
resistors connected with the reed switch in 2EOL configuration (see Fig. 5). They enable
the control panel to detect a tamper of the magnetic contact by monitoring the resistance changes on the zone. Each detector of this type must be connected to a
Individual magnetic contacts differ in the
Fig. 2 K-2 2E reed switch in plastic housing
housing style and the way of mounting. The K-1 2E is designed for surface mounting and the K-2 E & K-3 2E for flush mounting.
wherever required for controlling the status of doors, windows and/or other movable elements, e.g. for protection or monitoring of
access to particular sites, spaces, facilities;
Fig. 3 K-3 2E reed switch in metal housing
INSTALLATION – Fig. 4
The magnetic contact element containing the magnet should be mounted on the movable part, while the reed switch – on the stationary part of protected doors, windows, etc. Elements of the K-1 2E magnetic contact should be attached to the surface by means of screws, suitable glue, or a two-side self-adhesive tape. The K-2 E & K-3 2E magnetic contacts are designed for face mounting in such materials as wood or plastic (Fig. 4). The walls, the magnetic contact is to be fitted in, should be at least 10mm thick, so as to ensure adequate stability for the elements mounted. To make holes for the K-2 2E magnetic contact, use ø8mm drill, and for the K-3 2E magnetic contact – ø9mm drill. The K-2 2E is to be pressed in, while the K-3 2E, which has a thread, needs to be screwed in. The mounted magnetic contact elements can be reinforced with a suitable glue.
In order to ensure correct functioning of the magnetic contact, the distance between magnet and reed switch should not exceed 12–15mm for K-1 2E & K-2 2E, and 15–18mm for K-3 2E. Misalignment of the axes of magnet and reed switch in cylindrical magnetic contacts should not be greater than 10mm for K-2 2E and 12mm for K-3 2E.
• You are in no case allowed to shorten (cut short) the element containing the magnet. • Special care must be taken when installing reed contact part of the detector. It should not be hammered into the slot, because the fragile component inside the detector might be damaged then.
• When screwing the K-3 2E reed relay in, the wire will get twisted; to prevent it from damage, make sure that it has a sufficient spare length, or twist it in the opposite direction before installation so that it can straighten out when mounted.
Fig. 4 Example of face mounting of K-3 2E magnetic contact
HOOKUP – Fig. 5
Fig. 5 Connection of the magnetic contact with 2EOL resistor to the control panel.
Magnetic contact type .2EOL/NC Resistance.2x1.1kΩ Maximum switchable voltage of reed switch .200V Maximum switchable current .500mA Maximum continuous (non-switchable) current .1.5 A Rated power . 10 VA Minimum number of switchings under load
\\jciprod01\productn\C\COL\111-8\COL803.txtTHE STAY DILEMMA: EXAMINING BRAND AND GENERICINCENTIVES FOR DELAYING THE RESOLUTION OF The Hatch-Waxman Act encourages generic drug companies to chal- lenge the patents on brand name drugs by awarding the first generic chal-lenger 180 days of generic marketing exclusivity, a bounty often worth mil-lions of dollars. Challenging a patent usually trigge
Molecules 2007 , 12, 1092-1100 molecules ISSN 1420-3049 Biotransformations of Imbricatolic Acid by Aspergillus niger and Rhizopus nigricans Cultures Guillermo Schmeda-Hirschmann 1,*, Carlos Aranda 1,2, Marcela Kurina 3, Jaime A. Rodríguez 4 and Cristina Theoduloz 4 1 Laboratorio de Química de Productos Naturales, Instituto de Química de Recursos Natura